MAN0868-04-EN Specifications / Installation __________________________________________________________________________________________________________________________________________________________________ 12/19/2008 Page 1 of 3 ECN # 947 1 Specifications Specifications General Specifications Required Power (Steady State) 130 mA @ 24 VDC Required Power (Inrush) 30 A for 1 ms @ 24 VDC Primary Power Range 10 – 30 VDC Relative Humidity 5 to 95% Non-condensing Clock Accuracy +/- Seven Minutes/Month at 20C Operating Temperature -10°C to +60°C Terminal Type Screw Type, 5 mm Removable Weight 12 oz. (340.19 g) CE UL See Compliance Table at : http://www.heapg.com/Support/compliance.htm 2 Panel Cut-Out and Dimensions Note: Max. panel thickness: 5 mm. Refer to the User Manual for panel box information and a handy checklist of requirements. Note: The tolerance to meet NEMA standards is ± 0.005” (0.1 mm). 3 Ports / Connectors / Cables Note: The case of the XLt is black, but for clarity, it is shown in a lighter gray color. XLt OCS Model: HE-XT100 / HEXT240C000 / HEXT240C100 3.622 [92mm]3.622 [92mm]001XLE002Power Connector Power Up: Connect to Earth Ground. Apply 10 - 30 VDC. Screen lights up. Torque rating 4.5 – 7 Lb-In (0.50 – 0.78 N-m) CAN Connector Use the CAN Connector when using CsCAN network. Torque rating 4.5 – 7 Lb-In (0.50 – 0.78 N-m) To Remove Back Cover: Unscrew 4 screws located on the back of the unit and remove back cover.CAUTION: Do notover tighten screws when replacing back cover. Memory Slot: Uses Removable Memory for data logging, screen captures, program loading and recipes. Horner Part No.: HE-MC1 Serial Communications: MJ1: (RS-232 / RS-485) Use for Cscape programming and Application-Defined Communications. MJ2: (RS-232 / RS-485) Use for Application-Defined Communications. MJ1(RS-232 / RS-485)MJ2(RS-232 / RS-485)Memory Slot NET 1(CsCAN)PowerDIPSwitch Note – Your keypad overlay appearance may differ. Standard US/EU overlays pictured here for example. MAN0868-04-EN Specifications / Installation __________________________________________________________________________________________________________________________________________________________________ 12/19/2008 Page 2 of 3 ECN # 947 5 Wiring and Jumpers Wire according to the type of inputs / outputs used, and select the appropriate jumper option. • Use Only Copper Conductors in Field Wiring, 60/75° C 5.1 External DIP Switch Settings 6 MJ2 Pinouts in Half and Full Duplex Modes Wiring Specifications �For CAN wiring, use the following wire type or equivalent: Belden 3084, 24 AWG (0.2 mm2) or larger. 4 Serial Communications: MJ1: (RS-232 / RS-485) Use for Cscape programming and Application-Defined Communications. MJ2: (RS-232 / RS-485) Use for Application-Defined Communications. As seen when looking at the top of the XLt unit: DIPSW3: FACTORY USE ONLY (tiny bootloader firmware downloading). NOT TO BE USED FOR NORMAL OCS OPERATION. DIPSW2: MJ2 Termination (Default – none) DIPSW1: MJ1 Termination (Default – none) 001XLE037-R1The DIP Switches are used for termination of the RS-485 ports. The XLt is shipped un-terminated. To terminate, select one of the DIP Switches and configure it based upon the option that is desired. Pin MJ1 Pins MJ2 Pins Signal Direction Signal Direction 8 TXD OUT TXD OUT 7 RXD IN RXD IN 6 0 V Ground 0 V Ground 5* +5 60mA OUT +5 60mA OUT 4 RTS OUT TX- OUT 3 CTS IN TX+ OUT 2 RX- / TX- IN / OUT RX- IN 1 RX+ / TX+ IN / OUT RX+ IN 1 8 * +5Vdc 60mA Max MJ2 Half Duplex ModePin MJ2 Pins Signal Direction 8 TXD OUT 7 RXD IN 6 0 V Ground 5* +5 60mA OUT 4 TX- OUT 3 TX+ OUT 2 TX-/RX- IN/OUT 1 TX+/RX+ IN/OUT 18Pin MJ2 Pins Signal Direction 8 TXD OUT 7 RXD IN 6 0 V Ground 5* +5 60mA OUT 4 TX- OUT 3 TX+ OUT 2 RX- IN 1 RX+ IN 18MJ2 Full Duplex Mode* +5Vdc 60mA Max MAN0868-04-EN Specifications / Installation __________________________________________________________________________________________________________________________________________________________________ 12/19/2008 Page 3 of 3 ECN # 947 7 Safety 8 Technical Support For assistance and manual updates, contact Technical Support at the following locations: North America: (317) 916-4274 http://www.heapg.com email: firstname.lastname@example.org Europe: (+) 353-21-4321-266 http://www.horner-apg.com email: email@example.com No part of this publication may be reproduced without the prior agreement and written permission of Horner APG, Inc. Information in this document is subject to change without notice. Warning: Consult user documentation. Warning: Electrical Shock Hazard. This equipment is suitable for use in Class I, Division 2, Groups A, B, C and D or Non-hazardous locations only WARNING – EXPLOSION HAZARD – Substitution of components may impair suitability for Class I, Division 2 AVERTISSEMENT - RISQUE D'EXPLOSION - LA SUBSTITUTION DE COMPOSANTS PEUT RENDRE CE MATERIAL INACCEPTABLE POUR LES EMPLACEMENTS DE CLASSE 1, DIVISION 2 WARNING – EXPLOSION HAZARD – Do not disconnect equipment unless power has been switched off or the area is known to be non-hazardous. AVERTISSEMENT - RISQUE D'EXPLOSION - AVANT DE DECONNECTOR L'EQUIPMENT, COUPER LE COURANT OU S'ASSURER QUE L'EMPLACEMENT EST DESIGNE NON DANGEREUX. WARNING: To avoid the risk of electric shock or burns, always connect the safety (or earth) ground before making any other connections. WARNING: To reduce the risk of fire, electrical shock, or physical injury it is strongly recommended to fuse the voltage measurement inputs. Be sure to locate fuses as close to the source as possible. WARNING: Replace fuse with the same type and rating to provide protection against risk of fire and shock hazards. WARNING: In the event of repeated failure, do not replace the fuse again as a repeated failure indicates a defective condition that will not clear by replacing the fuse. WARNING: Only qualified electrical personnel familiar with the construction and operation of this equipment and the hazards involved should install, adjust, operate, or service this equipment. Read and understand this manual and other applicable manuals in their entirety before proceeding. Failure to observe this precaution could result in severe bodily injury or loss of life. When found on the product, the following symbols specify: � All applicable codes and standards need to be followed in the installation of this product. � Adhere to the following safety precautions whenever any type of connection is made to the module: � Connect the safety (earth) ground on the power connector first before making any other connections. � When connecting to electric circuits or pulse-initiating equipment, open their related breakers. � Do not make connections to live power lines. � Make connections to the module first; then connect to the circuit to be monitored. � Route power wires in a safe manner in accordance with good practice and local codes. � Wear proper personal protective equipment including safety glasses and insulated gloves when making connections to power circuits. � Ensure hands, shoes, and floor are dry before making any connection to a power line. � Make sure the unit is turned OFF before making connection to terminals. � Make sure all circuits are de-energized before making connections. � Before each use, inspect all cables for breaks or cracks in the insulation. Replace immediately if defective. This device complies with part 15 of the FCC Rules. Operation is subject to the following two conditions: 1. This device may not cause harmful interference. 2. This device must accept any interference received, including interference that may cause undesired operation.